I have an FP-1600 that had been powered off for several months. After power was applied the status led was on indicating that the unit was not configured. I configured the unit with Measurement and Automation Explorer and restarted the unit. Since the unit was restarted, I have been unable to communicate with it. I have tried to put the unit in reset mode but that apperars to fail also since the status LEd never comes on. The power, link and 100 Mbps indicators are all on and appear normal but I cannot communicate with the unit. All help would be appreciated.