I am trying to measure the Harmonic power from my cRIO. To do that I have used the Electrical Power suite advanced harmonic components. When I run the program the error code 363357 is shown due to the sample rate not being constant.
I would like to know how I can make the sample rate from the FPGA measurement constant please.
I am using the NI cRIO 9030, with NI 9227 and NI 9225 modules. Below is my FPGA VI.
Please help Thank you in advance.
Here is the VI in which the error occurs, the error, 363357, occurs after the first zero crossing VI.
I don't have LV 2015 right now but based on your description I would check if you are using the electrical power suite resampling you should also be using the electrical power suite harmonics functions.
The reason is the resampler will change the sampling frequency according to the mains frequency, that would be why it is changing.