Message Edited by hemmerling on 01-11-2007 12:08 AM
Thanks for your help. Tommy is coorect. The same AI-110 module has channels with timestamps that are hours, minutes and seconds different. There are a quantity of three (3) cFP-2120 modules on the same subnet each with theri own static IP address. cFP-2120-A has one AI-110. cFP-2120-B has three AI-110 and cFP-2120-C has one AI-110. Each cFP has their own backplane. Each cFP has the LV development PC as the time server (again a static IP).
I will write down some data to clearly show the issue that I have.
I also have come across another question: When one looks at all of the channels on the cFP-2120, you see the LEDs, Power (which source), Digital I/O There is another one called 'Temperature'. Is there a tmeperature sensor on the cFP-2120? I don;t recall reading this in the manual.
Message Edited by hemmerling on 01-11-2007 09:19 AM
I think our threads got crossed. I'm asking about timestamps be out of synchrtonization with cFP-2120 and cFP-AI-110.
Those are a lot of questions, hard to answer over the forum! I would recommend to contact your local NI-Office and maybe to get a visit from a sales engineer to talk about the best solution for your specific application.
Message Edited by Christian_M on 01-22-2007 10:14 AM